As a resident of Mechanicsville, you know how crazy the weather can be. For example, one day it can be a beautiful 60 degrees, and the next it could be raining and 30 degrees. Consequently, that’s why when you need affordable air conditioning and heating service in Mechanicsville, VA, you want a local HVAC company like Loving Air. Ultimately the difference is that Loving Air Specialists work hard to give each job their all while using their years of experience. Ready for the solutions to your HVAC problems? By all means, Give the HVAC Specialists Serving Mechanicsville at Loving Air a call today!
We could let our reputation as a trustworthy, budget-friendly, and reliable heating and cooling company speak for itself. However, if you’re in need of residential or commercial services there’s only one place to go. Lastly, The HVAC contractors serving Mechanicsville believe everyone should stay comfortable in their home or business. Ready for high-quality installations, repairs, or tune-ups? Get started with Loving Air today!
We recommend preventative heating tune-ups to keep your HVAC system in good order and to catch more costly repairs before they happen.Learn More
Is your heater on the fritz? Loving Air’s knowledge and affordable rates make us the top heater repair company in Fredericksburg.Learn More
Heat pumps are essential to the function of your HVAC unit. We install and repair heat pumps so your family can enjoy energy-efficient heat.Learn More
Whether you need your furnace repaired or replaced, Loving Air will be there to get your heating source up and running in no time.Learn More
Selecting a new heating unit can be daunting. Our experts will help you select the right make and model for your home, and install it at budget-friendly rates.Learn More
Programmable thermostats can help cut your energy bill and add an extra level of ease and comfort to you and your family’s life.Learn More
Ductless mini-split systems offer homeowners a cost-effective way to replace inefficient window AC units, space heaters, and so on.Learn More
If you need boiler maintenance, repairs, or installation services by the experts, you need Loving Air. We’ve got affordable HVAC services that will keep you cozy in your home.Learn More
Lack of cleaning, improper vent materials, or poor vent installation in dryer vents can lead to house fires.Learn More
Keep your family’s water warm and comfortable. Don’t waste money on your utility bill if you’re not getting warm water when bathing or washing your hands. We can help keep your water warm today!Learn More
$500 Off for One System Replacement.
$1500 Combined Off Two Systems Replacement.
Excellent and caring service
We are extremely satisfied with the service. Technicians were amazing. So professional and thorough. They were polite and found a problem that needed corrected since our home was built. We can’t say enough about Loving Air. I give them 26 stars.
Response from Loving Air, Inc.:
Darlene, We do love to take care of the community and provide a service that is best for them. Please let us know if you need anything else and have a great weekend
Response from Loving Air, Inc.:
Michael thank you for the review and we are glad James did a great job at giving you the information that you were looking for.
Response from Loving Air, Inc.:
Sean, Glad we took great care of you. Please let us know if there is anything else we can help you with.
Upon arrival filters are clean. Spoke with customer and they explained no issues at this time. Went to stat and stat was clean. Went to attic. Heat exchanger checked out good. Coil is clean, no leaks at this time.cleaned flame sensor. Gas pressures where 3.5IWC. Tested safetyâ€™s and they are working at this time. Blower has film on it, still recommend to clean. Wires all tight. Blower amped at 1.1amps. Drain line is clear. Spoke to customer about duct work and blower and customer wanted to fix duct work. Re did duct so it was not pinched off. Showed customer pictures and they are happy at this time. System is working well at this time of service.
Upon arrival, upstairs system. Filters are clear. Went to thermostat, system set to 79Â°, turned system down and went into attic. Coil is clean, found no leaks on coil. Drain line is clear. Blower is clear, amped at .9amps. Heat exchanger checked out in good shape. Wires all tight. Indoor unit is running well. Went outside, coil is clear. Contacter and capacitor checked out within specs. Fan amped at 1.1amps. Compressor amped at 6.43amps. Refrigerant levels where 75/280 psi. Disconnect wires are tight. Upstairs system is running good at this time but with its age it could fail at any time. Downstairs, turned system up, went into crawlspace. Coil is clean. Blower is clean, amped at 1.0amps. Drain line is clear. Wires are tight. Unit is level. Heat exchanger looks good at this time. Went outside, coil is clear. Wires are tight. Fan amped at 1.1amps. Compressor amped at 6.16amps. Refrigerant levels where 115/320. Contacter and capacitor checked out within specs. Disconnect wires are tig
Upon arrival started upstairs. Turned stat on cool. Went to attic, no ladder needed, filter was clean. Coil and blower are clean. Wires are all tight. Blower amped at .93amps. Drain is clear but is not a eztrap. Padpn does have pan safety in it. Leak searched indoor coil with no hits. Turned system back on and let it run. Went to garage unit, coil and blower are clear. Heat exchanger showing no signs of cracks. Leak searched coil with no hits but is very rusted. Brought customer out to see coil and explain what can happen over time. Wires all tight and drain is clear. Blower amped at 1.4amps. Went outside, upstairs outdoor, wires are tight. Contacter is working good. Capacitor (45/5) checked out at 45/5mfd. Fan amped at .53amps. Compressor amped at 5.53amps. Pressures are 115/325. Disconnect wires are tight. Coil is clear. Upstairs is working good at time. Downstairs outdoor, coil is dirty, fan amped at .31amps. Compressor amped at 3.99amps. Contacter and capacitor checked out withi
Arrived to the house and knocked on the front door, customer customer greeted us at the door and allowed us to enter inside. Asked customer if we could see the indoor unit and the thermostat. Customer then showed us through the house on where everything was located. Customer has goodman straight ac system located in the attic. Attic furnace Visually inspected the unit and the duct work and noticed some of the Supply flex duct work was kinked off feeding some of the upstairs bedrooms. Will quote to repair. Took and amp draw off indoor blower wheel of 5.4 which is in range per manufacturing specs. Inspected indoor blower wheeler and is slightly dirty will recommend a cleaning. Inspected indoor evaporator coil and is clean and free of debris at this time. Checked 12.5 run capacitor on the fan motor and got a reading of 12.6 which is in range per manufacturing specs. Indoor unit is running properly at this time. Outdoor unit Turned system in cooling to properly check charge, systems cha
Upon arrival found duct work for main truck laying on the ground, return has a water line threw it. Indoor blower and coil are very dirty. Coil is leaking oil. Outside unit, contacter is very pitted. Capacitor checked out ok. Fan amped at 1.3amps. Compressor amped at 6.8amps. System has refrigerant in it but with system being dirty and leaking can not be exact on charge. Priced up repairs for system and replacement. Customer wanted an email copy of proposal, he is going to speak wi5 home warranty company. Explained to customer price and availability is subject to change.
Upon arrival filter is clean, found unit is in garage. Shut power off and tried to restart system and found ignitor was bad. Checked heat exchanger for cracks and found non with the camera. Put ignitor in to check rest of operation. Coil is rusted but clear with no leaks at this time. Blower is clear, wires are tight. Started system, system came on blower amped at 1.1 amps. Gas pressures had to be adjusted from 5.0 to 3.5. Checked for carbon monoxide and got no hits. Let system run awhile and found no further issues. System is older and can fail at any time but at this time system is working. Spoke to home owner about membership and all and they already have an HVAC company they use but they could not get to them today
installed new system everything working properly
Performed maintenance on the attic system. Inspected blower assembly and evaporator coil for cleanliness, blower was slightly dusty and evaporator is clean and free of debris. Gave the blower assembly a slight cleaning in place. Amp draw on the blower motor is 0.7 which is in range with manufacture specs. Inducer motor is amping at 1.5 which is at max amperage, but is still functioning properly. Burners had a slight dust build up which I brushed away. Flue pipe is in good condition with no holes, cracks or rust. Gas pressure is at 3.5in wc. Heat exchanger is in good condition with no holes or cracks and very minimal rust. All wire connections are tight. Cleared all hoses. Condenser coil is slightly dusty on one side facing the home which I was able to brush clean. Contactor is in good condition with no pitting. Tested 35/3 dual run capacitor and it is within range, ready 34.7/3. Condenser fan motor is amping in the correct range with manufacture specs at 0.7. Compressor is also opera