As a resident of King George, you know how crazy the weather can be. For example, one day it can be a beautiful 60 degrees, and the next it could be raining and 30 degrees. Consequently, that’s why when you need affordable air conditioning and heating service in King George, VA, you want a local HVAC company like Loving Air. Ultimately the difference is that Loving Air Specialists work hard to give each job their all while using their years of experience. Ready for the solutions to your HVAC problems? By all means, Give the HVAC Specialists Serving King George at Loving Air a call today!
We could let our reputation as a trustworthy, budget-friendly, and reliable heating and cooling company speak for itself. However, if you’re in need of residential or commercial services there’s only one place to go. Lastly, The HVAC contractors serving King George believe everyone should stay comfortable in their home or business. Ready for high-quality installations, repairs, or tune-ups? Get started with Loving Air today!
We recommend preventative heating tune-ups to keep your HVAC system in good order and to catch more costly repairs before they happen.Learn More
Is your heater on the fritz? Loving Air’s knowledge and affordable rates make us the top heater repair company in Fredericksburg.Learn More
Heat pumps are essential to the function of your HVAC unit. We install and repair heat pumps so your family can enjoy energy-efficient heat.Learn More
Whether you need your furnace repaired or replaced, Loving Air will be there to get your heating source up and running in no time.Learn More
Selecting a new heating unit can be daunting. Our experts will help you select the right make and model for your home, and install it at budget-friendly rates.Learn More
Programmable thermostats can help cut your energy bill and add an extra level of ease and comfort to you and your family’s life.Learn More
Ductless mini-split systems offer homeowners a cost-effective way to replace inefficient window AC units, space heaters, and so on.Learn More
If you need boiler maintenance, repairs, or installation services by the experts, you need Loving Air. We’ve got affordable HVAC services that will keep you cozy in your home.Learn More
Lack of cleaning, improper vent materials, or poor vent installation in dryer vents can lead to house fires.Learn More
Keep your family’s water warm and comfortable. Don’t waste money on your utility bill if you’re not getting warm water when bathing or washing your hands. We can help keep your water warm today!Learn More
$500 Off for One System Replacement.
$1500 Combined Off Two Systems Replacement.
I’m very happy
Ryan was so informative and thorough and fixed all my issues professionally. Saving his card and will be using his service always.
Ryan from Loving Air was professional, courteous & knowledgeable. He showed me exactly what he was talking about & explained it so I knew what was happening.
It was a great pleasure to have technician, Shawn, out to our home to fix our AC. He was incredibly thorough & personable. We will definitely be requesting him again for any future work needed. Thank you.
Tech was very knowledgeable and thorough in his trouble shooting. He explained everything to me and answered all my questions so that I understood the information. He wasn’t in a hurry and he was very thorough. He tested everything out to ensure it was all within specifications. I was given a report with all the data captured. In the end he gave me a game plan on what we needed to do. Very impressed.
Knowledgeable tech. Explained everything.
Response from Loving Air, Inc.:
Sam, Thank you for letting us know our service is great. Have a great weekend.
We are very happy with the service and support that we routinely receive from Loving Air. We contracted them to replace both of our AC units and have had no problems since. They return twice a year and inspect everything. The team is great. Jeremy our service tech is awesome and thorough. I appreciate him taking the time to explain everything to me including my options as I am a member of the loyalty program. Keep up the great work, my family is in your hands and we couldn't be happier. Paul
Response from Loving Air, Inc.:
Paul, WOW what a great review. When I started this my main focus was customer service and my team has done a great job at making sure that we provide the best customer service possible. Please let us know if you need anything else. Have a great day. Shane Loving
Jeremy provided excellent service. He is courteous and efficient.
Response from Loving Air, Inc.:
Ed, Thank you for the great review. We love to hear these great reviews. Please let us know what else we can do for you. Shane Loving
. Upon arrival spoke with the customer. She had a new unit put in and wanted it looked at. The filter is a little bit dirty. She is going to get a new one. The blower housing is clean. The blower motor amped at 1.27. The electric heat strips amped at 23.97 and 23.59. This is in range. Inspected low and high voltage wiring on unit. All wiring is good and tight. The thermostat is working properly. The system is working properly at this time. Customer asked me to look at the outdoor. Another company told her it would need a part. Found where the outdoor unit was. The Unit is missing. Someone took the outdoor and the customer didn’t know. She said she doesn’t have money for the design consultant to come out and doesn’t have insurance on the house. She said she has window units for when it gets hot. I informed her we do not work on window units. Went over membership options with her. She declined.
When arrived to the home I greeted the customer at the front door. After asking a couple questions customer took me downstairs to where we found the air handler to the main level system of the house. Remove the door to the air handler and noticed the blower motor was not running. Confirmed we had 244v on the high-voltage side of the motor and confirmed or sending proper low-voltage from circuit board to blower module let motor cool down for a few minutes replugged all wiring, harnesses and blower motor tries to run backwards and forwards until immediately shutting off. Customer needs repairs being after hours call will start repair estimate. Will need to be completed. When can confirm pricing and availability for replacement variable speed, blower motor and send estimate to customer for approval
<br> <br> Upon inspection found kink in gas supply line 3/8<br> Unbend line and re-light pilot.<br> Turned gas valve on and turned fire place back on , fire place is back on at this time . <br> Cycled fire place on low and high fire , fire place is working properly at this time.<br> Propane Gas tank is less than 20% full , tank needs to be refilled.
Arrived at customers residence and was greeted by customer and was led to attic unit thermostat on the second floor and found that thermostat was showing error codes of 184.07 and 184.08.. The 184.08 code is dealing with a compressor issue and took an amp draw of 8.6 with the maximum RLA being 11.5.. found no issues with compressor at this time. 184.07 is dealing with restrictions such as dirty blower and dirty filters and evaporator coil restrictions found no such issues at this time.. Also possible up and down of electrical blower.. Customer stated that the same codes appeared a couple of years ago when the system was reset no problems arises until today. I reset the system and have consistently been monitoring system and have had no coding on thermostat or outdoor led screen at this time.. outdoor is clean â€¦ Fan motor and blade are clean. Fan motors has no leaks in the seals at this time. Checked thermostat for possible communication errors and none were found at this time. Res
Arrived at customers residence and was greeted by customer and was led to the thermostat put system in auxiliary heat mode.. inspected heater kit and found it to be clean .. inspected blower motor and wheel and both are operating normally at this time.. Surge protector is operating according to manufacturers specifications at this time. Emergency heat amp draw is 13.2 amps at this time.. inspected condensate drain and it is clear at this time..Condensate pump is operating normally and according to manufacturers specifications at this time.. All electrical connections are tight and neat to the components.. And wire nut connections are tight and neat at this time. Indoor disconnect is tight and is o-resting normally and according to manufacturers specifications at this time.All tape joints and duct work joints are tight and neat and no evidence of air leaks at this time.. inspected 20x20x1 and 14x14x1 both were replaced by customerâ€¦. Inspected outdoor heat pump and the coils for ups
Heating inspection AHU Inspected high and low voltage wiring, all electrical wiring is intact and tight at this time. Performed complementary refrigerant leak search, no leaks found at this time. Inspected evaporator coil, coil is clean at this time. Inspected heat strips contactor, contactor is pitting and causing charr on contactor, this component is prone to failure at anytime. Built and presented estimate to customer, customer kindly declined the repair estimate at this time. Inspected his trips, heat strips are pulling 20/20 Amps at this time inspected blower motor, housing and wheel, all is clean and working properly at this time Motor is spinning freely at this time Blower motor amp draw @1.35 Return temp 74F Supply temp 113F Inspected cabinet for cleanliness, cabinet is clean at this time. Clear drain line, drain is clean at this time. Inspected air filter , air filter is clean at this time. HP Inspected high and low-voltage wiring, all electrical wiring is intact and
Arrived at customers residence and found heat pump system with R22 refrigerant to be non working at this time.. Turn thermostat to heat mode and went downstairs to basement and found blower motor to be very dirty and heavy oily dirty and debris covering vent side of blower motor.. The oily residue is evidence of a blown seal in motor. Also found blower wheel to heavily compacted with dirt and debrisâ€¦ Inside air handler cabinet to have bacterial growth â€¦ found evaporator coil to be dirty as well.. also found heavy dirt and debris,on the,outside of condensate drain.. Condenser coil outside is dirty with debris and grass clippings. Was unable to get system to operate due to bad blower motor. Based on the age and condition of system I would strongly suggest total replacement of the system also factoring R22 refrigerant.. Refigerant lines are 5/8 and 3/8 diameter lines.
Upon arrival spoke with customer and she has been happy with the system. Pulled cover off and checked all wires and made sure everything was tight. Made sure gas pressure was correct for what the book called for. Made sure temperature set points where correct and tested water line temps. Made sure exhaust was working properly. Cleaned out spider webs from inside of unit for customer. Made sure everything was working properly and explained unit for customer. Priced up membership for just the boiler, but explained we could look at the other systems as well (customer said there was 6 systems). Customer wants to speak to her husband about membership. System is working good at this time of service.
Upon arrival spoke with customer and they have had no issues at this time. Turned system on, went to basement, indoor coil and blower are clear. No leaks on coil. Wires all tight. Heat strips amped good. Drain is clear. Duct work is tight. Went outside, wires all tight. Fan amped at .68amps. Compressor amped at 6.32amps. Contacter and capacitor checked out good. Refrigerant levels where 125/348. Pressures are within manufacturing specs. Priced up some safetyâ€™s for the system as well as a U. Light to keep any growth off system. Customer did not want anything done at this time of service. Also explained to customer with age of equipment anything can happen but they did not want a design consultant at this time.
Arrived customer home and was greeted by customer.. Was led to the basement to the water heater and inspected elements on the water heater and found they are operating normally.. proceeded to flush water heater and found light sediment present in the tank after flush.. Inspected dryer vent and found very light dusting customer would like to clean dryer vent when return for Spring maintenance service..