As a resident of King George, you know how crazy the weather can be. For example, one day it can be a beautiful 60 degrees, and the next it could be raining and 30 degrees. Consequently, that’s why when you need affordable air conditioning and heating service in King George, VA, you want a local HVAC company like Loving Air. Ultimately the difference is that Loving Air Specialists work hard to give each job their all while using their years of experience. Ready for the solutions to your HVAC problems? By all means, Give the HVAC Specialists Serving King George at Loving Air a call today!
We could let our reputation as a trustworthy, budget-friendly, and reliable heating and cooling company speak for itself. However, if you’re in need of residential or commercial services there’s only one place to go. Lastly, The HVAC contractors serving King George believe everyone should stay comfortable in their home or business. Ready for high-quality installations, repairs, or tune-ups? Get started with Loving Air today!
When your air conditioning and heating system begins to malfunction beyond repairs, it may be time to consider a replacement. With continuously improving technology, oftentimes the newer equipment will save you more money on your energy bill. At Loving Air, we make sure to give you the best and most efficient option for HVAC systems that will fit your home. We’ll perfectly size your system so you get the most from your HVAC units. Don’t be fooled, larger equipment is not always better, and can end up costing more money. Make sure to consult a professional before making a big purchase on your HVAC system. Schedule an appointment and learn more about our HVAC deals!Contact Us
Tired of troubleshooting your HVAC system? At Loving Air, we provide stress-free repairs on your heating and cooling system. Our team has experience with all kinds of makes and models and has the right tools to get your equipment back in working order. Sometimes maintenance just isn’t enough, but we are dedicated to giving your family expert services. Contact us today to learn about some signs it may be time to repair your HVAC system.Contact Us
Whether your system requires cooling or heating maintenance, you’ve got you covered. Our technicians have over 20 years of knowledge and experience for checkups and tune-ups on your HVAC equipment. No matter what type of heating or cooling system you have in your home, we’ll make sure it’s running efficiently and economically. We also provide regular maintenance to ensure your machine is running properly. Give us a call and we’ll tell you about our membership maintenance plans that will save you money, and up the lifespan of your HVAC system.Contact Us
Proactive AC tune-ups can save you money in the long run. We offer monthly maintenance packages to cut your energy costs.Learn More
Our team of experts has the knowledge and affordable rates to repair your AC unit. No matter how big the job is, we’ve got you covered.Learn More
Selecting a new AC unit can be daunting. Our experts will help you select the right make and model for your home, and install it at budget-friendly rates.Learn More
Heat pumps are essential to the function of your HVAC unit. We install and repair heat pumps so your family can enjoy energy-efficient heat.Learn More
Programmable thermostats can help cut your energy bill and add an extra level of ease and comfort to you and your family’s life.Learn More
Ductless mini-split systems offer homeowners a cost-effective way to replace inefficient window AC units, space heaters, and so on.Learn More
Lack of cleaning, improper vent materials, or poor vent installation in dryer vents can lead to house fires.Learn More
Keep your family’s water warm and comfortable. Don’t waste money on your utility bill if you’re not getting warm water when bathing or washing your hands. We can help keep your water warm today!Learn More
Great service… professional and prompt. Outstanding!!!
Always a pleasure and excellent service.
I’m very happy
Ryan was so informative and thorough and fixed all my issues professionally. Saving his card and will be using his service always.
Ryan from Loving Air was professional, courteous & knowledgeable. He showed me exactly what he was talking about & explained it so I knew what was happening.
It was a great pleasure to have technician, Shawn, out to our home to fix our AC. He was incredibly thorough & personable. We will definitely be requesting him again for any future work needed. Thank you.
Tech was very knowledgeable and thorough in his trouble shooting. He explained everything to me and answered all my questions so that I understood the information. He wasn’t in a hurry and he was very thorough. He tested everything out to ensure it was all within specifications. I was given a report with all the data captured. In the end he gave me a game plan on what we needed to do. Very impressed.
arrived at customers residence and was greeted by customer. Customer and lead me to the back of the house to enter basement area to check the downstairs system at this time. Inspected thermostat and found that it is functioning properly at this time. Upon arrival to outdoor unit for downstairs system found vines growing out through condenser coil at this time. inspected condenser pool for outdoor heat pump and found that the pool has vines going through the outer facing of the air conditioner. Megaohmed compressor, and found that it is reading 300 mega ohms, which is good at this time. Inspected fan motor and blade. Fan motor is showing heavy rust due to being exposed to the elements. Found no evidence of leaking seals at this time fan blade is clean and without any issues at this time. Inspected disconnect for outdoor unit and it is tight and neat to the side of the home at this time. Refrigerant charge is on the light will be inspecting indoor coil for possible leaks. Outdoor unit i
arrived at customers residence and was greeted by customer. Customer led me to the thermostat thermostat in cool mode and thermostat is functioning properly at this time. Customer then let me to the basement where the indoor coil and furnace are located. Inspected 16 x 25x1 filter, and it is clean at this time. Inspected gas line going into furnace found that it is tight and neat without any visible defects at this time. Manual gas supply valve is functioning properly at this time. Electrical connections are tight and neat to the components and wire nut connections. Are tight and neat at this time. Inspected 4 inch flue pipe and it is tight and neat to the furnace at this time. All tape joints and ductwork joints are tight and need at this time. Inspected Remi halo and it is functioning properly at this time. Inspected condensate drain and it is clear at this time. Ez traps safety switch is functioning properly at this time. CS one safety switch on secondary drain is functioning prope
All wiring is tight and in good condition. The condensate pump is working properly at this time. All water safeties are working properly at this time. The condensate drains are cleared. I completed a complimentary refrigerant leak search on the systems. No leaks present at this time. I completed our check sheets and emailed them to the customer. The systems are working properly at this time. The customer wanted an estimate for a new water heater. I prepared a quote.
found only a few things today that I wanted to bring to the customers attention. I was unable to talk to the customer about these options today because he was not here. Only the daughter was here to let me in and to help me out with anything I needed to find. I will be emailing these options to the customer. Both units are running well at this time and all other information is in my check sheet which I have also emailed to the customer.
Arrived at customers residence and was greeted by customer and was led to the thermostat and it is functioning properly at this time.. Inspected refrigerant lines and they are tight and neat at this time and Arma cell insulation is intact and without any visible defects at this time. Electrical connections are tight neat to the components and wire nut connections are tight and neat at this time. Inspected 50 and 35 amp circuit breakers and both are functioning properly at this time. Both have 244.3 volts in and out at this time.. All tape and duct work joints are tight and neat at this time. Replaced old uv light with a new uv photo max uv light and it is functioning normally at this time. Inspected ez trap safety switch and it is functioning properly at this time..Inspected control box on fan motor and it is functioning properly at this time..Condensate drain is clear at this time. Condensate pump is functioning -roperly and according to manufacturers specifications at this time. I
Arrived at customers residence and was greeted by the customer and was led to the thermostat to put it in cool mode and then was led to the basement to the unit. Indoor unit came on but outdoor unit.Proceeded to the outdoor unit and applied refrigerant gauges on system and found that the system is flat on charge at this time.. Performed leak search and found that there is a large leak in the condenser coil called for Territory Manager to come to customers residence to evaluate my findings and Customer has agreed to meet tomorrow morning at 11 am..
Upon arrival customer showed location of thermostat and filters which were clean at this time. When inspecting upstairs system found that the indoor coil was leaking from a soldering repair from previous company on coil. Showed and provided customer with options to address the issue. When looking at the outdoor unit found oil residue on the motor shaft. The outdoor coil had debris build up around but rinsed it clean. Customer needs time to talk to wife and potential may need territory manager to provide a with options on replacing the system. Do to work customers need time to review and coordinate a date. 14x14x1 20x20x1 kitchen 16x25x1 basement 14x14x1
Arrived at customers residence and was greeted by customer and was led to the outdoor unit to re braze copper line to the compressor.. brazed copper line into side of compressor and cut out old bi flow filter drier and replaced it with new filter drier.. Charged system with nitrogen to check for leaks in the system maintained 300 psi of nitrogen and held pressure for 20 mins. After finding no leaks proceeded to put vaccum pump in line with system.. Started up system and it is functioning normally at this time.
Arrived at customers residence and was greeted by customer and was led to the thermostat for the upstairs unit and it is operating normally at this time. Inspected evaporator coil and it its clean at this time.. inspected 2- circuit breakers and they are operating normally at this time with 245.1 volts going in and,our,at this time. Inspected blower motor and heel and they are both clean at this time. Ins-e Ted evaporator coil and it is clean at this time.. inspected Cs1mssfety switch and it is functioning properly at this time..ins-extend 7.5 uf capacitor and it is within range of manufacturers specifications at this time.Electrical connections are tight and neat at this time and Arma cell insulation is intact and is without visible defects at this time. Checked refrigerant charge with gauges and found that the charge is flat at this time due to bad braze joint on liquid line entering into compressor housing..