When it comes to Culpeper, you never know what the weather will be like. From humid summers to bone-chilling winters, keeping up with your HVAC system ensures your family stays comfortable no matter the time of year. That’s why when you need affordable air conditioning and heating service, you want the local HVAC Specialist in Culpeper at Loving Air.
Our reputation as a trustworthy, budget-friendly, and reliable heating and cooling company proceeds us. No matter whether you need residential or commercial services, we believe everyone should stay comfortable in their home or business. Ready for high-quality installations, repairs, or tune-ups? Get started with the HVAC Specialist in Culpeper at Loving Air today!
Proactive AC tune-ups can save you money in the long run. We offer monthly maintenance packages to cut your energy costs.Learn More
Our team of experts has the knowledge and affordable rates to repair your AC unit. No matter how big the job is, we’ve got you covered.Learn More
Selecting a new AC unit can be daunting. Our experts will help you select the right make and model for your home, and install it at budget-friendly rates.Learn More
Heat pumps are essential to the function of your HVAC unit. We install and repair heat pumps so your family can enjoy energy-efficient heat.Learn More
Programmable thermostats can help cut your energy bill and add an extra level of ease and comfort to you and your family’s life.Learn More
Ductless mini-split systems offer homeowners a cost-effective way to replace inefficient window AC units, space heaters, and so on.Learn More
Lack of cleaning, improper vent materials, or poor vent installation in dryer vents can lead to house fires.Learn More
Keep your family’s water warm and comfortable. Don’t waste money on your utility bill if you’re not getting warm water when bathing or washing your hands. We can help keep your water warm today!Learn More
Thanks for quality service
Jimbob is spectacular
Thorough and professional.
James was professional, courteous, polite and FAST!!!
Awesome service from the lady on the phone to James...everyone was so polite, helpful, and thorough!
The best this man needs a pay raise
The technician was very polite and knowledgeable. Took his time and very thorough. He explained everything he was doing and what he found.
All wiring is tight and in good condition. The systems are clean. The refrigerant pressures are in correct range per manufacturer specifications. The capacitors and contactors are in good condition. I completed a complimentary refrigerant leak search on the systems. No leaks found at this time. I completed our check sheets for the systems. The systems are working properly at this time. The customer declined options at this time.
All wiring is tight and in good condition. The heat exchanger is in good condition. I completed a complimentary refrigerant leak search on the system. No leaks found at this time. The refrigerant pressures are off a little due to the weather but are close to correct range per manufacturer specifications. I completed our check sheet for the system and presented club membership options for the system. The customer signed up for our club membership.
Arrived to the customers home and greeted her at the front door. Spoke with the customer about how the systems have been performing and if had any questions or concerns. On the call had spoke with Brian who asked for this one system check to be performed on the upper level heat pump system. When got to the air handler in the attic found air handler locked out on a blower motor. Fault. Cycled high-voltage to system to reset code. When blower motor turned on ECM will spin for a second or two then clunk off. Repeat this process until locks out on error code. quoted customer for part and labor ECM blower motor replacement excepted estimate ordered part with manufacture. Need to have office check on customer’s lower level system post install from June 23, when schedule the return trip for motor install please let them know. Spoke with Kelly before leaving job today.
During my inspection today, the customer greeted me at the door. She let me come inside and inspect her equipment. She showed me around all the equipment. The customer explained to me that they do not use the oil heat anymore. So I was not going to inspect that today. The only thing on the Oil Furnace that I was inspecting was the blower. Which checked out good. I did a leak search in evaporator coil cleaning. I checked the outdoor unit. Everything on the outdoor unit look good. I wasn’t able to check it fully because it is a straight AC unit. And I wasn’t able to run it with it being this cold outside. It is about 38° outside. I checked out all that I could. I talk to the customers mother about maybe replacing the system with a heat pump system instead of an old furnace. I tried calling the customer directly but it went straight to voicemail. I did leave him a message. I will have Mike Manager call him and get with him on possibly replacing the system.
During my inspection today, the customer greeted me at the door. I had him explain to me any issues that he had with the new system. He said that he had no issues with the new system. I did get started in the basement where I checked out all electrical connections, and checked all components for cleanliness, and to make sure that they were free of damage. Everything checked out good in the heating mode on the air handler. I then made my way to the outdoor unit where I checked refrigerant pressures and electrical connections. As well as electrical components and motors. Everything was also free of debris and free of damage. At this time the outdoor unit is also operating properly and the heating mode. I asked the customer if you had any more questions before we wrapped up today he said no. I am giving the customer the option today to do a water heater combo, which includes a water heater flush, and a overall water heater inspection, and a UV photomax for indoor air quality purposes. Th
Inspected main level and split for upstairs bedroom. Main level found pressures slightly low to manufacture specification at this time no leaks were found on the system. Notified customer to keep eye on system if aux runs longer then normal. Split system found no leaks at this time filter clean free of debris returned to original setting.
Customers had water in dryer in past. We removed a wall cap and installed a new wall cap to prevent any moisture from entering from the outside. Confirm there is no water inside dryer vent at this time are using inspection camera inside dryer vent. Showed customer a couple pictures and we’ve decided to clean the dryer vent while on site today. Cleaned upper level dryer vent and return system to service
I arrived to the customers home and greeted her at the door. Spoke with the customer about how the system has been performing and she had any questions or concerns for me before getting started completed the maintenance inspection of the gas furnace, while visually inspecting all AC components, but did not run an AC mode today. Replace customer provided air filter and spoke about other services loving air provide such as water heater inspections and gas fireplace inspections. Completed maintenance inspection, checklist uploaded pictures, and videos and return system to service.
Arrived to the customers home and greeted him at the door. Spoke with the customer and how the system has been performing and I’ve had any questions at this time. Customer showed me a thermostat location, indoor and outdoor equipment. Completed today’s inspection of York heat pump system Found all operations and components within manufacturer specifications at this time. Completed maintenance inspection, sheet uploaded pictures and videos. Went over other services loving our offers to our membership customers. Returning system of the service.
Upon arrival customer showed location of thermostat and basement system. Inspected electrical connections which were tight and secured. Found inducer, gas valve, and blower amping correctly. The blower motor is clean free of debris when examining heat exchanger found it in good condition. Gas pressures in the correct range at this time. Examined scuttle which is operating properly at this time. Reviewed options with the customer at this time declined returned system to normal operation.