When it comes to Ashland, you never know what the weather will be like. From humid summers to bone-chilling winters, keeping up with your HVAC system ensures your family stays comfortable no matter the time of year. That’s why when you need affordable air conditioning and heating service, you want the local HVAC Specialist in Ashland at Loving Air.
Our reputation as a trustworthy, budget-friendly, and reliable heating and cooling company proceeds us. No matter whether you need residential or commercial services, we believe everyone should stay comfortable in their home or business. Ready for high-quality installations, repairs, or tune-ups? Get started with the HVAC Specialist in Ashland at Loving Air today!
Proactive AC tune-ups can save you money in the long run. We offer monthly maintenance packages to cut your energy costs.Learn More
Our team of experts has the knowledge and affordable rates to repair your AC unit. No matter how big the job is, we’ve got you covered.Learn More
Selecting a new AC unit can be daunting. Our experts will help you select the right make and model for your home, and install it at budget-friendly rates.Learn More
Heat pumps are essential to the function of your HVAC unit. We install and repair heat pumps so your family can enjoy energy-efficient heat.Learn More
Programmable thermostats can help cut your energy bill and add an extra level of ease and comfort to you and your family’s life.Learn More
Ductless mini-split systems offer homeowners a cost-effective way to replace inefficient window AC units, space heaters, and so on.Learn More
Lack of cleaning, improper vent materials, or poor vent installation in dryer vents can lead to house fires.Learn More
Keep your family’s water warm and comfortable. Don’t waste money on your utility bill if you’re not getting warm water when bathing or washing your hands. We can help keep your water warm today!Learn More
I appreciate the time Chris took to explain different things to me, and answer any questions I had. He was polite and professional. I will definitely request Chris for any future service I need. from Loving Air.
This was my 2nd appt. with Loving Air (first time for A/C maintenance). I switched to Loving Air last year in October because the company I had been using for over 10 years had a huge increase in their prices. Their service was hit or miss, depending on what tech they sent, so the price increase was not worth staying with them. I decided to try Loving Air. Mike, the tech, was a very nice guy. However, I found it odd that he came downstairs from the attic with a "part" in his hand, telling me it could potentially go bad (a capacitor). Then he took it out to his truck, and came back in telling me he had one available if I wanted him to replace it. I have never dealt with any HVAC company that actually took a part out of the system and then took it out to his truck. Yes, I have been scammed before so I am super cautious. My first thought was, "did he bring the same part back in"? "Did he put a different part back in my system?" I did not choose to replace it since the part was still working. Just because it was not at full capacity, I cannot afford to change parts prematurely. I would think all parts have the potential to go bad? I am a new customer so perhaps this is a normal practice with Loving Air that I am just not used to. The actual time it took to complete the service took longer than I am used to as well. But if it's just because Mike was being thorough, that is a good thing.
Technician was polite knowledgeable punctual and a high-level of confidence. Worked in a heavy downpour to fix the unit in a very short period of time. Very impressed with his dedication. Trey is an asset to the company.
Chris did a great job
Response from Loving Air, Inc.:
Wally, Chris loves doing a great job for our customers. Glad you saw the value in it as well. Have a great day and let us know if there is anything else we can do for you.
Upon arrival spoke with customer. Pilot was out, I re started fire place and let system run awhile. Made sure everything turned off and on correctly. Showed customer and gave him option for membership but he didn’t not want it at this time.
Upon arrival spoke with customer. He explained what he wanted done and we had done it before. He explained he had to go to work and gave me a check for the cleaning. Customer explained if any issues call him. Pulled both sides of the glass and cleaned them to the best we could. Took before and after pictures and videos. Turned gas on and tested fire place. Flue is working, gas valve is working well. Everything is clear at this time. Priced up to check up customers home systems, tried to call but had to leave message.
Upon arrival customer showed location of thermostat and filters which were clean at this time. When looking over the blower motor found the bearings had failed giving the motor play in the wheel. When inspecting capacitor found it had failed manufacture specifications. Inspected drains at this time which are clear and operating properly. Flame sensor is clean free of debris inducer amping properly clean free of debris. Went over with the customer how to operate the damper to find best comfort for customers liking. Went over options to address blower motor and capacitor for the attic system. At this time customer is trying to find paper work from previous company repairs.
Upon arrival spoke with customer and there where no issues. Stat was set correctly, indoor filter is clean. Coil and blower are clean. No leaks on coil. Wires all tight. Heat strips checked within specs. Unit is level. Duct is tight. Drain is clear. Safety is working. Turned stat on and had good split. Went outside, coil is clean. All electrical checked within specs. Motors checked within specs. Refrigerant pressures are within manufacturing specifications. Disconnect wires are tight. Fan motor showing no signs of oil. System is working well at this time. Spoke with customer about options and she declined at this time.
Arrived to the customers house and greeted them at the front door. Talked with the customer about how the systems been performing and if had any concerns at this time. Customer showed me the thermostat location filter, location, indoor and outdoor equipment complete and maintenance inspection and checklist went over repair options with customer who declined at this time. Emailed all information and return system to service.
Upon arrival spoke with customer. Turned stat up, filter is clean. Airflow is correct. Coil and blower are clean. Wires all tight. Drain line is clean and has safety’s. Duct work is tight. Unit is level. Went outside, cleaned coil. Wires all tight. Contacter and capacitor checked within manufacturing specifications. Fan motor amped at 1.1amps, with no signs of oil. Compressor amped at 5.38amps. Refrigerant levels where 97/352. Let system run awhile. Went inside and turned system to ac. Let system run for 15 mins with no issues. Disconnect wires are tight. Priced up some comfort options for customer but they did not want them done at this time of service.
Upon arrival spoke with customer and explained what I would be doing today and explained I would be going threw the entire system. Customer showed me where thermostat was and filters as well as indoor unit. Went into attic and started checking coil. Coil is clean and showing no signs of leaks. Drain line is clean. Heat exchanger showed no signs of cracks. Wires are all tight, safetyâ€™s are working. Cleaned flame sensor. Gas pressures are at 3.5IWC. Indoor unit is working properly at this time and is very clean. Went outside, coil is clean. Wires are tight. Disconnect wires are tight. Capacitor checked out at 35/5mfd. System has charge on it. Pushed contacter in to test system and fan motor and compressor both came on and ran good. Over all system is working great. Spoke with customer about a 90% furnace in an attic and the issues that come with it and she agreed she had issues at one time. I explained we had a â€œfixâ€ to try and help the drain line from freezing. Priced up fix as w
Upon arrival spoke with customer. Asked if there where any questions or concerns about the system and she explained no everything had been doing good. I explained what I would be going threw today and would be checking the vents and customer had no issues. Thermostat is clean, honeywell stat, and it is level. Stat is set to 68Â° cool, Turned system on to 74Â°. Went into hallway to evaluate the indoor unit. The coil is clean, along with the blower and found no leaks coming from the coil. Blower amped at 1.1amps. Wires are all tight. Drain is clear. Duct is clean and tight and The Drain is clear. All low voltage wires are tight. Went outside and evaluated the unit. Coil is clean. Wires low voltage and high are all tight with no burn marks or broken. Contacter is showing good at this time. Capacitor assessed at 45/5mfd and is a 45/5mfd capacitor. Fan motor amped at .68amps and showing no signs of oil leakage at this time. Compressor amped at 4.8amps. Refrigerant levels where found at
Upon arrival cleaned glass on both sides for fire place. Cleaned inside of fire place and tested gas and made sure fire place lit up. Gas pressures where 2.6IWC. Fire place is working good at this time of service, customer would also like to set up when he comes back in town to do a maintenance for his two systems. Tried to call customer and let him know system is good to go, but got no answer.
Upon arrival filter is clean, stat was on. Went outside, breaker was off. Started system up. Blower is clean, evap coil is clean. Condenser coil is clean. All wires are tight. Checked pressures to find txv shutting down showing it has failed. Checked windings on compressor after 3mins of run time and found compressor failing at this time as well. Believe txv failure has been causing stress on the compressor. Called Trane and system is under warranty until next year. Priced up repairs for customer along with a membership. Explained it would take 3-5days for shipping and everything. Customers wife owns the home so they have to talk it over. Showed customer and signed iPad in front of customer.