When it comes to Ashland, you never know what the weather will be like. From humid summers to bone-chilling winters, keeping up with your HVAC system ensures your family stays comfortable no matter the time of year. That’s why when you need affordable air conditioning and heating service, you want the local HVAC Specialist in Ashland at Loving Air.
Our reputation as a trustworthy, budget-friendly, and reliable heating and cooling company proceeds us. No matter whether you need residential or commercial services, we believe everyone should stay comfortable in their home or business. Ready for high-quality installations, repairs, or tune-ups? Get started with the HVAC Specialist in Ashland at Loving Air today!
We recommend preventative heating tune-ups to keep your HVAC system in good order and to catch more costly repairs before they happen.Learn More
Is your heater on the fritz? Loving Air’s knowledge and affordable rates make us the top heater repair company in Fredericksburg.Learn More
Heat pumps are essential to the function of your HVAC unit. We install and repair heat pumps so your family can enjoy energy-efficient heat.Learn More
Whether you need your furnace repaired or replaced, Loving Air will be there to get your heating source up and running in no time.Learn More
Selecting a new heating unit can be daunting. Our experts will help you select the right make and model for your home, and install it at budget-friendly rates.Learn More
Programmable thermostats can help cut your energy bill and add an extra level of ease and comfort to you and your family’s life.Learn More
Ductless mini-split systems offer homeowners a cost-effective way to replace inefficient window AC units, space heaters, and so on.Learn More
If you need boiler maintenance, repairs, or installation services by the experts, you need Loving Air. We’ve got affordable HVAC services that will keep you cozy in your home.Learn More
Lack of cleaning, improper vent materials, or poor vent installation in dryer vents can lead to house fires.Learn More
Keep your family’s water warm and comfortable. Don’t waste money on your utility bill if you’re not getting warm water when bathing or washing your hands. We can help keep your water warm today!Learn More
$500 Off for One System Replacement.
$1500 Combined Off Two Systems Replacement.
Technician was polite knowledgeable punctual and a high-level of confidence. Worked in a heavy downpour to fix the unit in a very short period of time. Very impressed with his dedication. Trey is an asset to the company.
Chris did a great job
Response from Loving Air, Inc.:
Wally, Chris loves doing a great job for our customers. Glad you saw the value in it as well. Have a great day and let us know if there is anything else we can do for you.
Upon arrival cleaned glass on both sides for fire place. Cleaned inside of fire place and tested gas and made sure fire place lit up. Gas pressures where 2.6IWC. Fire place is working good at this time of service, customer would also like to set up when he comes back in town to do a maintenance for his two systems. Tried to call customer and let him know system is good to go, but got no answer.
Upon arrival filter is clean, stat was on. Went outside, breaker was off. Started system up. Blower is clean, evap coil is clean. Condenser coil is clean. All wires are tight. Checked pressures to find txv shutting down showing it has failed. Checked windings on compressor after 3mins of run time and found compressor failing at this time as well. Believe txv failure has been causing stress on the compressor. Called Trane and system is under warranty until next year. Priced up repairs for customer along with a membership. Explained it would take 3-5days for shipping and everything. Customers wife owns the home so they have to talk it over. Showed customer and signed iPad in front of customer.
During my inspection I started with the outdoor unit. I found that the compressor was not running so the first thing I checked was proper voltage going to the system after confirming the correct voltage I checked the capacitor and it was reading zero on the 40 side of the 40/5 capacitor after replacing the capacitor I checked the unit started it up and watched the system run my refrigerant pressures were 125/387 with a 7.3Â° superheat and a 6.7Â° sub cooling these are the correct measurements are then took a Ampdraws of the outdoor system the compressor was 5.2 A in the condenser fan was .5 A these are also within manufacture specifications the outdoor unit is dirty and should be cleaned. The capacitor is still under warranty but the customer decided to replace the capacitor outside of the 10 year manufactures warranty due to price. I then made my way to the indoor unit were started by checking cleanliness of the evaporator coil and evaporator blower motor they were both dirty and a
Upon arrival filter is clean. Cleaned drain line and went over the bleach in the drain again. Coil and blower are clean. Blower capacitor is 10mfd. Wires are tight. Blower amped at 1.1amps. Indoor unit is working good. Went outside, contacter checked out good. Capacitor checked at 40/5mfd. Fan amped at 1.3amps. Compressor amped at 4.7amps. Refrigerant levels where 110/309. 60Â° outside, 72Â°. 8Â° subcool. Disconnect wires are tight. System is working good at this time, went over comfort options wih5h customer.
Upon arrival filter is clean. Coil is clear, blower is clear, wires are tight. Heat strips work good. Drain is clear. Blower amped at 1.1 amps. Indoor unit is working good. Went outside, coil is clear, wires are tight. Contacter and capacitor is within specs. Fan and compressor amped at 7.2amps. Refrigerant Levels checked out spot on per spec. Defrost this working properly. System is working good at this time. Customer signed up for membership.
Performed a maintenance on a gas fireplace. Removed glass face and cleaned debris from the burners. Confirmed thermocouple is in good condition and clean. Cleared all debris from fresh air intake and exhaust. Confirmed incoming gas pressure was correct. Checked outgoing gas pressure as well and it is at 2.7inwc. Gas valve recommends a range between 1.7-3.5. Relit the pilot and confirmed itâ€™s operation. Fireplace is burning better and cleaner that it has previously. Fireplace is operating properly at this time.