When it comes to the weather in Spotsy, it’s sporadic. One day it’s a beautiful, sunny 60 degrees. The next day, it’s raining and 30 degrees. As a local company, we know how important it is to be comfortable no matter how the weather changes. That’s why when you need affordable air conditioning and heating service, call Loving Air. We’re the local, leading HVAC contractors serving Spotsylvania, VA. We want you and your family to be comfortable in your home because as a family-owned business, we know how important it is. We offer our years of HVAC experience. Get the job done right the first time. Call the HVAC contractors at Loving Air!
Our reputation as a trustworthy, budget-friendly, and reliable heating and cooling company proceeds us. No matter whether you need residential or commercial services, we believe everyone should stay comfortable in their home or business. Ready for high-quality installations, repairs, or tune-ups? Get started with Loving Air today!
We recommend preventative heating tune-ups to keep your HVAC system in good order and to catch more costly repairs before they happen.Learn More
Is your heater on the fritz? Loving Air’s knowledge and affordable rates make us the top heater repair company in Fredericksburg.Learn More
Heat pumps are essential to the function of your HVAC unit. We install and repair heat pumps so your family can enjoy energy-efficient heat.Learn More
Whether you need your furnace repaired or replaced, Loving Air will be there to get your heating source up and running in no time.Learn More
Selecting a new heating unit can be daunting. Our experts will help you select the right make and model for your home, and install it at budget-friendly rates.Learn More
Programmable thermostats can help cut your energy bill and add an extra level of ease and comfort to you and your family’s life.Learn More
Ductless mini-split systems offer homeowners a cost-effective way to replace inefficient window AC units, space heaters, and so on.Learn More
If you need boiler maintenance, repairs, or installation services by the experts, you need Loving Air. We’ve got affordable HVAC services that will keep you cozy in your home.Learn More
Lack of cleaning, improper vent materials, or poor vent installation in dryer vents can lead to house fires.Learn More
Keep your family’s water warm and comfortable. Don’t waste money on your utility bill if you’re not getting warm water when bathing or washing your hands. We can help keep your water warm today!Learn More
$500 Off for One System Replacement.
$1500 Combined Off Two Systems Replacement.
Michael was excellent. Very thorough. Very personable.
Shawn provided conscientious, professional service! He was the first to clean out our outdoor units!
Cameron was on time, professional and knowledge. Answered all the questions we had about our unit.
Professional, prompt very respectful. He was a pleasure to meet.
The technicians came precisely on time. They were knowledgeable and able to tell me in layman's terms the state of my units. They were very thorough in checking everything. They were professional in attire and manner. I was impressed.
Mike was my tech this go round… was extremely knowledgeable and treated myself and my home with great care and respect. He explained everything he was doing and answered all my questions .
Preformed heating maintenance both systems. Confirmed air filters are clean. Confirmed upper level thermostat is working properly at this time. No major stored faults or alerts found. Put system into test mode and confirmed operation of all 3 stages of electric heat are operating within manufacturer specs 21.1/20.6/20.9 Took amp draw on the blower motor and found within specs 2.61 Found blower wheel clean and balanced. Found evaporator coil clean and free of any debris. Drains are clear and safety working properly. Found refrigerant levels within manufacturer specs 100/340 Took amp draw on the compressor an is within specs 6.4 Condenser fan motor amped within specs also .44 Confirmed defrost is working properly at this time. Confirmed thermostat on lower level is working properly at this time. Pulled and cleaned flame sensor and inspected the burners. Confirmed all pressure switch tubing is free of any obstructions. Pressure switches and safeties are working properly. Took amp draw on
Preformed heating maintenance on gas furnace. Confirmed filters were clean and thermostat is working properly. Reset customer light in the humidifier control from customer replacing water pad. Pulled and cleaned the flame sensor and inspected the burners. Confirmed all pressure switch tubing is clear of any obstructions. Checked gas pressure and found high adjusted back to spec 3.5inwc. Confirmed all pressure switches and safeties are working properly. Took amp draw on inducer motor and found within spec 2.8 Took amp draw on the blower motor 5.5 and is within specs. Capacitor is within recommended range. Cleared furnace drain and found flu with proper fall an intact. Returned to service
. Upon arrival customer showed me where the heatpump ran for 30 minutes them brought the aux heat on and the temp in the house satisfied then the heat pump ran for another couple hours and then the aux heat came on. Reset the stat and went through the settings. All settings are correct. Hooked the stat up to Wi-Fi so it could read the temp. Changed the setting so the aux heat would come on 2 degree difference. It was 67 in the house set the stat to 75 and it still would not bring the heat on. The aux heat was set to not come on above 50 and itâ€™s 39 outside. Called Ryan and we decided it was a bad thermostat. Will need to order one and come back and install it.
Preformed heating maintenance on upper level heat pump and lower level gas furnace. Found filters clean and upper level thermostat working properly. Found electric heat strips working within specs 41.3 Took amp draw on the blower motor and found within manufacturer spec 1.08 Found evaporator coil clean and free of any debris. Blower wheel is clean and balanced. Found refrigerant levels within specs 120/330 Found amp draw on compressor within range 8.2 Condenser fan motor amp draw is within spec .84 Lower level thermostat is updated and working properly with no stored faults in the history. Pulled and cleaned flame sensor and inspected burners. Confirmed all tubing is obstruction free an all safeties and pressure switches are working properly. Checked gas pressure in high and low fire low1.3inwc high 3.5 blower motor amps are within spec specs at this time 2.10 Blower wheel is clean and balanced. No issues or concerns at this time. Returned to service
I found the inducer motor getting power but it was not starting. I quoted a replacement motor. The customer signed for the repair. I picked the part up at the supply house. I returned and installed the motor. I tested operation. The pressure switch is working properly at this time. All wiring is tight and in good condition. All motor amps are in correct range per manufacturer specifications. The system is working properly at this time. The customer signed up for our club membership.
. Upon arrival spoke with the customer. She stated the mini split wasnâ€™t putting out warm air. She showed me the indoor unit. The system was running but blowing out 70 degree air. Took cover off the coil. The coil is very rusted. Leak searched the coil and found leaks. Went and got customer and showed her. Went to outdoor unit. Leak searched the outdoor and didnâ€™t find any leaks at this time. The Refrigerant pressure was 55. This is low. Called the design consultant out and scheduled for Today. Called east coast to get price on coil. She said she would call me back with pricing. The system is low on refrigerant and the coil is leaking. Informed customer we can add refrigerant but thereâ€™s no warranty on that and it could leak out today.
Preformed heating maintenance on gas furnace. Confirmed air filter was clean also confirmed thermostat is working correctly. Started with pulling and cleaning the flame sensor and inspected all burners. Confirmed all tubing is intact and clear of any obstructions. Confirmed all safeties and pressure switches are working correctly. Took amp draw on inducer .46 which is within manufacturer specs. Took amp draw on the blower motor and found within spec 4.90 Found capacitor is within its recommended range. Confirmed gas pressure is set correctly 10.5inwc checked heat exchanger and found no signs of corrosion or any cracks. Gave customer options for system upgrades. Returned to service
I started my inspection at the furnace. I found the flame sensor bad. I completed a visual inspection with my camera on the heat exchanger. I found two cracks in the heat exchanger. I showed the customer my findings. I completed a complimentary refrigerant leak search on the system. I found refrigerant leaks in both suction and liquid service valves. I meghommed the compressor and it is in caution just below red (Bad). I called the supply house to begin the process of obtaining price and availability on the parts needed for the repairs. Since this is a major repair I called to schedule an appointment for a design consultant to visit the customer and go over repair options. Appointment: 11/17/22 11-2pm.
. Upon arrival spoke with the customer. He showed me where everything was. Started with the attic system first. Turned the thermostat to heat. Went to indoor unit. Inspected evaporator coil. The coil is clean. Leak searched the coil and didnâ€™t find any leaks at this time. Inspected the blower motor and housing. The blower housing is clean and free of debris. The blower motor is amping at 1.25. This is in range per manufacture specifications. The electric heat strips amped at 20.93 and 21.32. Both are in range and working properly. Inspected low and high voltage wiring. All wiring is good and tight. The drain is clear. The drain safeties are working properly. All visible duct work is good and secure. The filter is clean. Went to outdoor unit. The Refrigerant pressures were 100/342. This is in range per manufacture specifications at this time. The compressor amped at 5.83. The condenser fan motor amped at .62. Both are in range at this time. Tested defrost. The defrost cycle is working